The selection of the safety valve is determined by the operating pressure to determine the nominal pressure of the safety valve, the operating temperature to determine the operating temperature range of the safety valve, the constant pressure value of the calculated safety valve to determine the constant pressure range of the spring or lever, and then the safety valve is determined according to the medium used. The material and structure type of the valve, and then calculate the throat diameter of the safety valve according to the discharge amount of the safety valve. The following are general rules for safety valve selection. (l) Hot water boilers generally use non-closed slightly open safety valves
with wrenches. (2) Steam boilers or steam pipelines generally use non-closed full-opening safety valves with wrenches. (3) For liquid incompressible media such as water, a closed micro-opening safety valve or a safety relief valve is generally used. (4) High-pressure feedwater generally uses closed full-open safety valves, such as high-pressure feedwater heaters, heat exchangers, etc. (5) Compressible media such as gas generally use closed full-open safety valves, such as gas storage tanks, gas pipelines, etc. (6) Class E steam boilers generally use dead-weight safety valves. (7) Pulse-type safety valves are generally used in large-diameter, large-displacement and high-pressure systems, such as temperature reduction and pressure reduction devices, power station boilers, etc. (8) Built-in safety valves are generally used in train tankers, automobile tankers, and storage tanks that transport liquefied gas. (9) Hydraulic safety valve is generally used on the top of the oil tank, which needs to be used in conjunction with the breathing valve. (10) Pilot-operated safety valves are generally used for underground drainage or natural gas pipelines. (11) A safety return valve is generally used on the liquid phase return pipeline at the outlet of the tank pump in the LPG station. (12) Vacuum negative pressure safety valves are generally used in systems that may generate negative pressure or negative pressure during operation. (13) Bellows safety valves are generally used for containers or pipeline systems with large fluctuations in back pressure and toxic and flammable. (14) For systems with a lower freezing point of the medium, an insulation jacket type safety valve is generally used.
If you are a types of industrial valves fan, you definitely want to enjoy the best possible. The that you choose plays a major role with the kind of experience you have when using it.
We are a provider of a various number of services that include . Search our website by valve application types of industrial valves product line or category to find what you are looking for.
is something that has been around for a few decades now, enjoying it's heyday back in the types of industrial valves.