During the use of the valve, there are often some troubling problems, such as the valve is not closed tightly, and the valve is not closed tightly. What should I do? The following introduces several treatment methods for internal leakage of the regulating valve. 1. The zero position setting of the actuator is inaccurate, and the fully closed position of the valve is not reached. Adjustment method: 1) Close the valve manually (it must be confirmed that it is completely closed); 2) Close the valve manually again with a little force; 4) Then adjust the limit. 2. The valve is a push-down closing type, the thrust of the actuator is not large enough, and it is easy to reach the full-closed position when there is no pressure, but when there is a downward thrust, the upward thrust of the liquid cannot be overcome. , so it is not closed. Solution: replace the actuator with large thrust, or change to a balanced valve core to reduce the unbalanced force of the medium. 3. Internal leakage caused by the manufacturing quality of the electric regulating valve, the valve manufacturer does not strictly control the valve material, processing technology, assembly technology, etc. in the production process, resulting in unqualified grinding of the sealing surface and no products with defects such as pitting and trachoma. Completely eliminated, resulting in internal leakage of the electric regulating valve. Solution: Rework the sealing surface. 4. The control part of the electric control valve
affects the internal leakage of the valve. The traditional control method of the electric control valve is through mechanical control methods such as valve limit switches and over-torque switches. Since these control components are affected by ambient temperature, pressure and humidity, Cause valve positioning inaccuracy, spring fatigue, uneven thermal expansion coefficient and other objective factors, resulting in internal leakage of the electric control valve. Solution: Readjust the limit. 5. The internal leakage caused by the debugging problem of the electric control valve is affected by the processing and assembly process, and the electric control valve generally has the phenomenon that the electric control valve cannot be opened electrically after it is manually closed. If the stroke of the electric control valve is adjusted to be smaller by the action position of the upper and lower limit switches, the electric control valve will not be closed tightly or the valve will not be opened. The torque switch protects the action; if the action value of the over-torque switch is adjusted to a larger value, there will be accidents that the deceleration transmission mechanism or the valve is damaged, or even the motor is burned. In order to solve this problem, usually, when debugging the electric control valve, manually shake the electric control valve to the end, and then shake it in the opening direction to set the lower limit switch position of the electric door, and then open the electric control valve to the fully open position to set the upper limit. Switch position, so that the electric regulating valve will not appear the phenomenon that the electric valve cannot be opened after the manual closing is tight, so that the electric door can be opened and closed freely, but it will cause the electric door to leak. Even if the adjustment of the electric control valve is ideal, because the action position of the limit switch is relatively fixed, the medium controlled by the valve will continue to scour and wear the valve during operation, which will also cause internal leakage caused by the valve being closed loosely. Solution: Readjust the limit. 6. The cavitation corrosion of the valve caused by the wrong type selection causes the internal leakage of the electric control valve. The cavitation is related to the pressure difference. When the actual pressure difference △P of the valve is greater than the critical pressure difference △Pc that produces cavitation, cavitation occurs. In the process of cavitation, when the bubble bursts, it releases huge energy, which has a huge destructive effect on throttling components such as valve seat and valve core. Generally, the valve operates for three months or even less time under cavitation conditions, that is, the valve suffers from damage. Serious cavitation corrosion, resulting in valve seat leakage as high as more than 30% of the rated flow, which is irreparable. Therefore, electric valves for different purposes have different specific technical requirements, and should be reasonably selected according to the system process flow Electric regulating valves are critical. Solution: Carry out process improvement and choose multi-stage pressure-reducing or sleeve regulating valve. 7. The internal leakage caused by the scouring of the medium and the aging of the electric regulating valve, after the electric regulating valve is adjusted and running for a certain period of time, due to the cavitation of the valve and the scouring of the medium, the wear of the valve core and the valve seat, and the aging of the internal parts, etc. , there will be a phenomenon that the stroke of the electric control valve is too large and the electric control valve is not tightly closed, resulting in a larger leakage of the electric control valve. As time goes on, the leakage of the electric control valve will become more and more serious. Solution: Readjust the actuator, and perform regular maintenance and calibration.
Technology is a foundational component of today's fast-paced business environment. Lianke Valve Co.,Ltd. who are digital natives are especially equipped to harness technology's power to establish, promote and grow our businesses.
Helping our customers manage document workflow and increase efficiency through best-in-class valve application and services. Fostering the growth and development of our employees.
Lianke Valve Co.,Ltd. has developed its range of products around its own market research, which discovers customers' precise needs.