The solenoid valve is composed of a solenoid coil and a magnetic core, and contains a valve body with one hole or several holes. When the coil is de-energized and unable to operate, the flow of fluid cannot be stopped, or it is suddenly cut off. Causes the fluid direction to change incorrectly. Solenoid valve is controlled by electromagnetic, as long as the power is off, it will not work. The electromagnetic components of the solenoid valve are composed of fixed iron core, moving iron core, coil and other components; the valve body part is composed of sliding valve core, sliding valve sleeve, spring base and so on. The solenoid coil is directly mounted on the valve body, which is enclosed in a sealed tube, forming a compact and compact combination. The solenoid valves
commonly used in our production include two-position three-way, two-position four-way, two-position five-way and so on. Let’s talk about the meaning of the two positions first: for the solenoid valve, it is energized and de-energized, and for the controlled valve, it is on and off. Solenoid valve installation attention 1. When installing, pay attention to the arrow on the valve body should be consistent with the flow direction of the medium. Do not install in places where there is direct dripping or splashing. The solenoid valve should be installed vertically upward; 2. The solenoid valve should be guaranteed to work normally within the fluctuation range of the power supply voltage of 15%-10% of the rated voltage; 3. After the solenoid valve is installed, there should be no reverse pressure difference in the pipeline. And it needs to be energized several times to make it suitable for temperature before it can be officially put into use; 4. The pipeline should be thoroughly cleaned before the solenoid valve is installed. The incoming medium should be free of impurities. A filter is installed in front of the valve; 5. When the solenoid valve fails or is cleaned, a bypass device should be installed to ensure the continuous operation of the system. Solenoid Valve Troubleshooting The failure of the solenoid valve will directly affect the action of the switching valve and the regulating valve. The common fault is that the solenoid valve does not work, and should be checked from the following aspects: 1. The solenoid valve wiring head is loose or the wire head falls off, and the solenoid valve cannot be powered , can fasten the wire ends. 2. If the solenoid valve coil is burned out, the wiring of the solenoid valve can be removed and measured with a multimeter. If the circuit is open, the solenoid valve coil will be burned out. The reason is that the coil is damp, causing poor insulation and magnetic leakage, resulting in excessive current in the coil and burning, so it is necessary to prevent rainwater from entering the solenoid valve. In addition, the spring is too hard, the reaction force is too large, the number of coil turns is too small, and the suction force is not enough, which can also cause the coil to burn out. In emergency treatment, the manual button on the coil can be turned from the '0' position during normal operation to the '1' position to make the valve open. 3. The solenoid valve is stuck: the fitting gap between the spool valve sleeve and the valve core of the solenoid valve is very small (less than 0.008mm), which is generally assembled in a single piece. When mechanical impurities are brought in or there is too little lubricating oil, it is easy to get stuck. . The treatment method can be used to poke the wire through the small hole in the head to make it spring back. The fundamental solution is to remove the solenoid valve, take out the valve core and the valve core sleeve, and clean it with CCI4, so that the valve core can move flexibly in the valve sleeve. When disassembling, pay attention to the assembly order of each component and the external wiring position, so as to reassemble and connect correctly, and also check whether the oil spray hole of the lubricator is blocked and whether the lubricating oil is sufficient. 4. Air leakage: Air leakage will cause insufficient air pressure, which makes it difficult to open and close the forced valve. When dealing with the failure of the solenoid valve of the switching system, an appropriate time should be selected, and the solenoid valve should be processed when the power is lost. If the processing cannot be completed within a switching gap, the switching system can be suspended and dealt with calmly. The above is my explanation of the installation precautions and troubleshooting of the solenoid valve. Lianke Valve Co., Ltd. is a company dedicated to the innovative manufacturing of valves. If you don't understand anything about today's content, you can come to the company's website for consultation, and the editor will explain it to you online from time to time.
Technology is a foundational component of today's fast-paced business environment. Lianke Valve Co.,Ltd. who are digital natives are especially equipped to harness technology's power to establish, promote and grow our businesses.
There is always a question of how to types of industrial valves, but have you ever thought about the price point? Go to Lianke Valve to get cost effective offer.
Lianke Valve Co.,Ltd. will do this by managing our business with integrity and the highest ethical standards, while acting in a socially responsible manner with particular emphasis on the well-being of our teammates and the communities we serve.